(sequence) Heading Description
For the condition of all facilities between stations P
time, the duration to be reported is the elapsed time
that all the affected facilities were deenergized. See
entry for the 4th day of the month at 0850 hours.
1625 hours illustrate the procedure for recording outages
of different durations for the various components of a
system sectionalized between terminal breakers like the
outage duration to be indicated for the complete P-Q
line is a series of zeros. For all intermediate components
between P and Q (line sections, taplines, and/or stations),
the outage duration to be indicated is the actual time
each facility was deenergized.
For the condition of one or more breaker and/or relay
operations discovered during routine rounds of
inspection at unattended stations, "MOM" should be
indicated in this column (see entries on sample form
Indicate by station designation (ADP abbreviation in
number, the breaker(s) tripped during the outage.
Use individual entry on separate line for each breaker
designation with associated relay information.
If the entry concerns a non-Reclamation facility (line, plant,
or station), or operation of Reclamation equipment through
which connection is made to a "foreign" utility, indicate
that utility, using the approved code designation
leave space blank.
Show relay type, as designated by device number on
station single-line diagram. If more than one relay
operated, use individual entry on separate line for
information for each relay. If the outage did not result
from relay operation but from manual operation of a
breaker or switch, enter "MANUAL" in this column.
If multiple target indications are possible on a particular
relay, show the relay target(s) indicated, such as "I" for
Instantaneous, "T" for Time-delay, ";Zl" for Zone 1, "Z-2"
for Zone 2, "TT" for Transfer Trip, etc. If identification
(FIST 1-3 12/89)