APPENDIX B. - Continued
Unit 5 was removed from service on 24th of the month. The rotor was pulled
and cleaning is commencing. A small section of the stator winding is being
coated with new insulating varnish to see if we can control the amount of
oil oozing from the coils. If the test is successful, we will coat the
entire winding during the next maintenance period. The upper guide bearing
was removed and large new cracks were observed in the babbitt. The spare
bearing was removed from storage, and is being sent to a machine shop for
boring and cutting oil grooves into the babbitt.
C. MISCELLANEOUS MAINTENANCE
Remodeling of the Office Building lobby is continuing. At the end of the
month, all new walls have been installed, trim is finished, and painting
is beginning. The utility room is complete.
The maintenance crew began the repair of the North Side Canal on 23rd of
the month. The ice in the canal had built up to 18 inches thick and the
first step was to remove an area of ice to work in. The work area was
lined with sandbags, and pumped dry. Excavation of the defective concrete
D. PERSONNEL CHANGES
No personnel changes this month.
No accidents occurred during the month.
The monthly safety meeting was held on the 26th of the month. Discussion
centered on fire extinguishers and piezometer well readings during the
Powerplant Operators received a total of 37 hours of training on various
subjects during the month.
G. NOTABLE OCCURRENCES
A promotion panel was convened to consider the candidates for the Facility
Manager position on the project.
92 (FIST 1-3 12/89)